responsibility of the design professional who must review the
specific project for its applicability before using or
specifying NUSIG guidelines.
NUSIG manuals of designs are pre-calculated from 0.05g through
1.00g in increments of 0.05g.
Unless otherwise shown by SMACNA or NUSIG, provide detailed
structural calculations for VA's review on design of hangers,
supports, anchor bolts, and connections. Show sizes, spacing, and
length for securing to structural members, and length and sizes of
welds anchored to steel members.
Where SMACNA or NUSIG details are incomplete or not
applicable, show complete seismic restraint requirements and
coordinate with the specifications. Coordinate mechanical work
with architectural and structural work. Special provisions and
details may be required.
Piping Plans and Sections: Show the locations of required
restraints with reference to SMACNA, NUSIG, or special
restraint details, whichever is applicable.
Equipment Restraints: Show special details where required. Pay
particular attention to suspended equipment.
Submit calculations required under the Contract to include the
following systems and equipment:
Soil, Waste and Vent
Hot Water Generation
Recommendation regarding the necessity for installing insulation
on the domestic water and horizontal storm drainage piping for the
Water analysis, including pH, total hardness as CaCO3, total
dissolved solids, and alkalinity.
PLUMBING FIXTURE SCHEDULES
conjunction with and superseding data found in the reference plumbing
code. Plumbing fixtures are described in Master Specification 15450,